The XEB-30 Fluorescent Emergency Ballast allows the same
fixture to be used for both normal and emergency operation when
used in conjuntion with an AC Ballast. If used in an emergency
only fixture, no AC ballast is necessary. In the event of a power
failure, the XEB-30 instantly switches to the emergency mode
and operates one or two of the existing lamps for 90 minutes. The
unit contains a battery, charger and inverter circuit in a single can.
The XEB-30 must be mounted next to or on top of the fixture,
and is U.L. Listed for factory installation or retrofit applications.
The XEB-30 can be used with most 2' - 8' lamps, providing an
initial output of 1450 - 3500 lumens for one or two lamps.
TECHNICAL SPECIFICATIONS Input Voltage 120/277V, 60Hz
Input Wattage 3.5 Watts
Lamps Operated: 17W-215W, 2'-8' single and bipin, T8, T10,
and T12, HO and VHO, Rapid Start, Slimline, and 4 pin 13, 18,
26 U-lamp, Circline compact fluorescent lamps.*
Emergency Operation (1) 2'-8' or (2) 2'-4' 90 minutes
Initial Illumination 1450 - 3500 Lumens
Initial Illumination 1450 - 3500 lumens
Approval U.L. Listed
Weight 93/4 lbs
Operating Temperatur 0o to 55o C
FEATURES U.L. Listed for factory or field installations
Will cold start and operate all specified lamps
High temperature, maintenance free, nickel-cadmium battery
Painted steel case
Dual voltage 120/277V, 60Hz
Includes one piece LED indicator light and test switch
Meets or exceeds all National Electrical Code and Life Safety
Code Emergency Lighting Requirements
90 minute emergency operation
24 hour recharge time
Mounting Center 15.9"
The Exit Sign Warehouse XEB-30 is warranted for five (5) years from date of purchase. Warranty covers only Exitronix emergency ballasts
installed as directed, and used under normal conditions. Warranty does not cover physical damage, abuse, or acts of God.
U.L. 924 listed for factory installations or field retrofit applications. Emergency illumination time exceeds the National Electric
Code (NEC), Life Safety Code (NFPA-LSP), and U.L. 924 90 minute requirements.
REMOTE MOUNTING The maximum allowable remote mounting distance is 50 ft. from the lamp.
When battery packs are remote mounted, the remote distance cannot exceed 1/2 of the distance from ballast to lamp, as specified
XEB-30 SAMPLE SPECIFICATIONS
Emergency lighting shall be provided by using a standard fluorescent fixture equipped with an XEB-30 fluorescent emergency
battery pack. The XEB-30 shall consist of a high temperature, maintenance free nickel cadmium battery, charger board and an
electronic circuit enclosed in a 9.4" x 2.4" x 1.5" vandal resistant, painted steel case. A long life LED charge/indicator light and
test switch shall be included. The XEB-30 shall operate most 17W-215W, 2'-8' single and bipin, T8, T10, and T12, HO and
VHO, Rapid Start, Slimline, and 4 pin 13, 18, 26 U-lamp, circline compact fluorescent lamps. The XEB-30 shall provide reduced
illumination for a minimum of 90 minutes in the emergency mode with a total initial output of up to 3000 lumens. The XEB-30
meets or exceeds all NEC and Life Safety Code Emergency Lighting Requirements and is U.L. Listed. The XEB-30 is warranted
for five (5) years from the date of purchase.
FLUORESCENT EMERGENCY BALLAST 500 starting at $42.50
FLUORESCENT EMERGENCY BALLAST 650 w/ 1/2 FLEX CONDUIT AND TEST SWITCH starting at $115.00
FLUORESCENT EMERGENCY BALLAST 700 starting at $59.99
FLUORESCENT EMERGENCY BALLAST 1400 starting at $61.00
FLUORESCENT EMERGENCY BALLAST 650 starting at $65.00